Type 1+2 for 2 MPP Tracker
The surge protective device comes as an upgrade kit and can be installed into the inverter connection area in a few minutes.
|Nominal voltage||1000 VDC|
|Highest continuous voltage||1200 VDC|
|Connection cross section||PV 6mm², Signal 0,5mm²|
|Fault indicator||Mechanisch Rot|
|Remote message signal||Integriert|
1) Since April 2019, DIN VDE 0100-712 requires that a DC fuse be installed on PV systems. In DIN VDE Appendix ZB Section712.534 DE, it is stipulated that the surge protective devices be fitted on the DC side as close to the inverter as possible.By installing the DC SPD 8.2 type 1+2 M surge protective device, these standard requirements are fulfilled.
2) A Fronius Solar.web account is required